Click on the photo to enlarge
Relays temporary are used for time control in industrial and home automation systems (e.g. ventilation, heating, lighting, signaling, etc.).
The contact remains in position 11-10 until the relay is switched on. After supplying the supply voltage, the contact is switched to position 11-12 and the set working time is measured. After the time has elapsed, the contact returns to position 11-10. Reactivation of the relay operating mode is possible after disconnecting the supply voltage and switching it on again. Note!
* When the power supply is switched on, the system does not react to changing the time range settings.
* Operation with the newly set time range takes place after switching off and re-enable
* When the power is turned on within the set time range, it is possible to smoothly adjust the time within the time setting value.   ; ON - when the power supply is on, the contact is permanently switched on in position 11-12.
OFF - when the power is on, the contact is permanently switched on in position 11-10.